Payment & Shipping Terms:
|Application:||Nuclear Power Plant||Lead Time:||In Stock|
|Con 6DS1311-8AEtrol System:||1503VC-BMC4||Weight:||4lbs|
ALLEN BRADLEY CONTACTOR 1502-VC4DBDA-0 SER E w/ 1503S-4C NEW AB1503VC-BMC4
This document contains information for the Allen-Bradley Bulletin 1503VC IntelliVAC™ control module. The Bulletin 1503VC is used to control the Allen-Bradley Bulletin 1502 vacuum contactors that are a significant component of the Bulletin 1500/1900 Centerline Medium Voltage Motor Controllers offered by Rockwell Automation. An IntelliVAC control module may also be provided as a loose component, for application with a Bulletin 1502 contactor by a third party (OEM). Description IntelliVAC is an efficient and flexible solution for controlling medium voltage vacuum contactors used in motor starter and feeder applications. IntelliVAC may be used to control both 400 and 800 Amp contactors. Electrically held and mechanically latched contactor types can be controlled with IntelliVAC.
A wide range of supply voltage (110 – 240 V AC 50/60 Hz, 110 - 250 V DC) allows implementation in multiple applications
Consistent vacuum contactor pick-up time (at a given supply voltage) ensures repeatable performance Selectable vacuum contactor drop-out time improves coordination with upstream power fuses
Electronic altitude compensation (400 A only) eliminates mechanical compensation required for altitudes above 1,000 meters (800 A contactors include a user-friendly altitude adjustment)
Power loss ride-through (TDUV) allows the vacuum contactor to remain closed during short power loss (may require an optional external capacitor, dependant on ride-through time)
The IntelliVAC may be ordered as an OEM component. This allows the OEM to mount the components in a configuration most suitable to the motor controller equipment layout. Care must be exercised to ensure the IntelliVAC has adequate ventilation provided around it. Refer to Figure 3.2 for mounting the IntelliVAC. It is recommended that a minimum of 1.5 inches (38.1mm) of free air space be provided between the IntelliVAC and any solid barrier above or below. The OEM is responsible for controller fusing, motor overload protection, control devices (eg. Start/Stop push buttons), and wiring between the IntelliVAC and 1502 vacuum contactor (using optional wire harness). Wiring and mounting for optional items, such as TDUV Capacitor are also the OEM’s responsibility. Refer to Figure 3.3 or 3.4 for basic connections. An optional EMI filter is required to meet CE EMC requirements (refer to Chapter 6 for recommended type).
|ABB||DTCA717A 61430001-WH||SCHNEIDER||TSXP67455 TSX6740||GE||IC3000CS200M|
|ABB||DSBC 173||SCHNEIDER||TSXAEM1613 TSX-AEM1613||GE||DS200SDCIG2AFB|
|ABB||PAB02 P70870-4-0369059 369059A10||SCHNEIDER||TSXP4720||GE||531X111PSHAPG3|
If you have any question pls do not hesitate to contact us.We can supply all kind of the automaiton parts,if you want to purchase parts pls send the parts model to my mail, I will prompt reply you asa I receive the mail.Hope anyone enquire from us.
Waiting for your inquiry.
Contact Person: miya